PROFIBUS dp/v1 fieldbus coupler 12 mbaud digital and analog signals. Part #, Manufacturer, WAGO. GTIN, Condition, New. Quantity . Accessory Type: Fieldbus Coupler. Current Rating: mA. Current Rating: mA. External Depth: mm. External Depth: mm. External Width: 51mm. Hi everyonei’m a beginer and i’m trying to connect wago I/O system with CPU CDP But I Don’t know where i did the mistake i.
|Genre:||Health and Food|
|Published (Last):||2 January 2013|
|PDF File Size:||19.5 Mb|
|ePub File Size:||2.39 Mb|
|Price:||Free* [*Free Regsitration Required]|
For modules capable of diagnosis the diagnosis message can be suppressed or released channel for channel or module for module. See the attached picture.
Attention Marginal conditions must always be observed to ensure smooth operation. The wavo supply is intended both for the system and the field units. Any use of this manual which infringes the copyright provisions stipulated herein, is not permitted.
7500-333 Always plug a bus end module onto the end of the fieldbus node! Hi dchartier thank you a lot for all this helpful informations. Wago LED diagnostics.
Byte Information 15 0 0 0 0 0 1 1 1 Header byte 7 Byte status information incl. A structure is added to the device status for each faulty slot.
When handling the modules, ensure that the environment persons, workplace and packing is well grounded. The others receive manufacturer specific parameters.
Analog outputs contain 4 byte parameterisation data. I believe the following link is the one you showed originally; it contains a sample configuration for the as a Profibus slave to a SDP master: Your manual failed to awgo To fix, insert a screwdriver into the top groove of the locking disc and press.
The diagnostic buffer wagl the Wwgo CPU should contain messages detailing the source of the problem. Display elements 3. This is described in the manual I proposed earlier. A fault is cyclically displayed with up to 3 blink sequences. See the attached picture, and the original text for more explanations. The line type B also described in the EN 50 is an old type and should no longer be used.
Warning Always observe this information to prevent damage to the device.
WAGO : User manual
If you have trouble doing so, Save As Text the contents 750-33 the buffer and attach the messages that seem to relate to a bus fault to your next reply, we might be able to help you find the source of the problem with more precision.
Hello karim; Have a look at the Diagnostics section of the manual, the first part shows how to evaluate an error based on the diagnostic LED status: A maximum of bytes of data is transmitted from the master to the coupler or from the node to the output data.
By the way, the end module is required to terminate the IO bus of the Wago modules, but is wwago part of wwgo configuration. S Segment A network is generally structured by Router or Repeater in various physical network segments.
Input modules counter are followed by 2 bytes which are reserved for future options.
What’s missing? Tell us about it.
The female contacts on the right-hand side of the fieldbus coupler and the bus modules are designed as spring contacts to protect against accidental contact. Hello Karim; The manufactiuring number inscribed on the side of the module contains the FW L number of the module.
The current capacity of the power contacts is 10 A max. Analog inputs are followed by 2 bytes reserved for future options. In the Federal Republic of Germany, various national regulations for the installation in explosive areas must be taken into consideration. New question published by pharaz is split to a separate thread with the subject wago ?
This channel is allocated to the coupler. The right hand LED C signals the supply to the field side, i. 750-33
probleme with wago and S CPU CDP – Entries – Forum – Industry Support – Siemens
Select the configuration that is closest to the range of FW in th configuration settings. Tell us about it. Attachment Wago sample configuration.
Server Serving device within a Client Server System.